“Reliable Family Run (Husband & Wife Formed)”
"Twice recommended by"Time Out"
Basic Knowledge - The complete electric underfloor heating system for new concrete screeds.
Ecoflex In-screed underfloor heating cables have a rating of 15W/linear metre and are an economical solution for new screed floor constructions. The first step is to determine the number of W/m2 that you require for your installation. This could be provided by calculating the heat losses from the room you intend to heat. This figure will depend on the standard of insulation in the building.
Underfloor electric Installation
Before Commencing, the entire sub-floor should be swept clean and be free from any sharp objects. If laying onto foil backed insulation ensure the ara is dust free to enable a good fix.
It is good practice to plan your installation using a sketch marking your laying pattern and planning the postions for the floor sensor, the connection box and thermostat.
Attatch the eco-fix band to the sub-floor or insulation using fixing nails or high impact adhesive tape. The Eco-fix bands should be spread evenly across the floor at intervals of 750mm. A 75mm border should be left around the perimeter of the room. Do not remove the cable from the drum before laying as it will twist and make the installation difficult.
The heating cables (orange cables) must not touch each other and should never cross. The heating cable must not be cut or shortened and the joint between the cold tail and the heating cable must not be bent or put under strain.
The floor sensor for the thermostat should be positioned between 2 heating cables approximately 500mm from the wall. The black flexible conduit provided should always be used to install the floor sensor probe. Once laid the heating cable should be covered with a minimum of 50mm sand and cement screed.
Before and after covering the heating cable with screed the cable resistance should be checked against the
A fully qualified electrician must now make the final connections to the mains supply and install the thermostat. The thermostat should be installed in the room to be heated. For bathrooms the thermostat will be a floor sensing only model and must be placed outside the room but as close to the installation as possible. Finally the electrician should check for continuity of the floor sensor and retest the resistance of the cable. A further insulation test should be carried out in accordance with IEE regulations.
Reliable Family Run Chislehurst Underfloor Heating Company Chislehurst Bromley BR1,BR2,BR3 Central Heating Engineer Farnborough Park BR4,BR5,BR6,BR7,BR8 Petts Wood SE21,SE23,SE24,SE25,SE26,SE27,SE28 Kent,Croydon,CR1,CR0,CR2 Twickenham TW1,TW2 Bromley, Croydon, Kent, Bromley, Kent BR1, Bromley BR1, Bickley, Downham, gas engineer BR2 Keston, BR2 Hayes boiler repair services BR2, Bromley Common Solar hot water , heating systems installer Elm Walk BR2 Shortlands, Orpington BR6, Farnborough Park Solar heating company, BR3 Beckenham , BR3 Eden Park , BR3 Elmers End West , Wickham BR4 , Orpington BR5, St.Mary Cray , BR5 Petts Wood , BR6 Orpington, BR6 Farnborough Park boiler installer, BR6 Downe , BR6 Pratt's Bottom , Bromley BR6, Chelsfield BR6, Well Hill Elm Walk , BR7 Chislehurst 24 Hrs boiler replacement , Elmstead BR8, Farnborough Park Underfloor heating repair, underfloor heating specialist, underfloor heating repair, wet underfloor heating, underfloor heating specialists, underfloor heating pipes Swanley, Bromley BR7 good plumber, solar power ,commercial cooker maintenance and repair Twickenham-Richmond-recommended-plumbers-TW1-Twickenham-St.Margarets, Strawberry-Hill-Richmond-TW2-Whitton-Strawberry-Hill-Solar-panel-heating , TW3-TW4-Hounslow-TW5-Heathrow-TW6-Isleworth-TW7-Isleworth, TW8-Osterley-Brentford-Hounslow-TW9-North-Sheen-Kew-Richmond, TW10-Ham-Petersham-TW11-TW12-Hampton-Richmond-TW13-Feltham, Hanworth-Hounslow-TW14-Hatton-TW15-Ashford-TW15-Spelthorne-TW16, Sunbury-on-Thames-TW17-Spelthorne-TW17-Shepperton-TW18-Staines-Egham, central-heating-boilers-TW18-Hythe-Spelthorne-TW18-Runnymede-TW19, Stanwell-TW19-Wraysbury-TW19-Spelthorne-TW19-Windsor-Maidenhead-TW20, Egham-TW20-Runnymede-Twickenham-Richmond-gas-engineer-UB1-Southall , Ealing-Hayes-Harlington-Heathrow-International-airport-heating-contractors-UB4, Yeading-Hayes-Hillingdon-UB5-plasterer-Northolt-Ealing-Greenford-UB6-Perivale-Ealing, Greenford-UB7-West-Drayton-Harmondsworth-Sipson-Yiewsley-Longford-UB8, Uxbridge-Cowley-Hillingdon-UB9-Denham-Uxbridge-South Bucks-Hillingdon, UB10-Hillingdon-Twickenham-UB11-Stockley Park-Uxbridge-Stanwell-TW19-Wraysbury, underfloor heating installer,
Reliable Family Run Chislehurst Underfloor Heating Company Chislehurst Bromley BR1,BR2,BR3 Central Heating Engineer Farnborough Park BR4,BR5,BR6,BR7,BR8 Petts Wood SE21,SE23,SE24,SE25,SE26,SE27,SE28 Kent,Croydon,CR1,CR0,CR2 Twickenham TW1,TW2